Welcome to the aboveground storage tank forum, a bulletin board dedicated to tanks, fuel tanks, plastic tanks, fuel storage tanks, and above ground storage tanks (AST) API650, API653 & UL142 aboveground storage tanks (AST) and chemical plastic tanks. Remember the forum is made up of volunteers from experts to beginners. Unfortunately, we cannot allow free commercialism that promotes products, services, or sites.
S.SHAHUL HAMEED on Plumbness level alowed in storage tank as per api-650 designBy: S.SHAHUL HAMEED 
Date: Saturday, February 26, 2011
Time: 4:15:15 AM
Kindly refer API650 Clause 7.5.2 Plumbness
a. The maximum out-of-plumbness of the top of the shell relative to the bottom of the shell shall not exceed 1/200 of the total
The out-of-plumbness in one shell course shall not exceed the permissible variations for flatness and waviness as
specified in ASTM A 6M/A 6, ASTM A 20M/A 20, or ASTM A 480M/A 480, whichever is applicable.